PTI 100/220...240 S POWERTRONIC INTELLIGENT S
PTi 100/220...240 S POWERTRONIC INTELLIGENT S
|Lamp wattage||97 W|
|Line current||0.49 A|
|Ignition voltage||4.5 kVp|
|Operating frequency||0.165 kHz|
|System wattage||106.00 W|
|Input voltage AC||220…240 V|
|Input voltage range AC||198…254 V|
|Mains frequency||50…60 Hz|
|Power factor λ||0.95|
|Inrush current||60 A|
|Max. no. of ECGs on circuit breaker 10 A||5|
|Max. no. of ECGs on circuit breaker 16 A||8|
|Protective conductor current||0.4 mA|
|U-OUT (working voltage)||250 V|
|Max. working voltage between LH and LL||250 V|
|Max. working voltage betw. LL/LH & earth||250 V|
|Max. capacitance of wire ECG/lamp||120 pF|
|Dimensions & weight|
|Mounting hole spacing, length||139.0 mm|
|Mounting hole spacing, width||74.0 mm|
|Cable cross-section, input side||0.5…2.5 mm²|
|Cable cross-section, output side||0.5…2.5 mm²|
|Wire preparation length, input side||10…11 mm|
|Wire preparation length, output side||10…11 mm|
|Product weight||350.00 g|
|Colors & materials|
|Ambient temperature range||-25…+55 °C|
|Maximum temperature at tc test point||80 °C|
|ECG lifetime||50000 h|
Areas of application
Ballast losses and lamp heat radiation can lead to heat accumulation in a completely closed case. Therefore it is necessary to ensure that the temperature at the measuring point tc of the ECG does not exceed the maximum value.
For safety reasons disconnect the device before replacing the lamp!
Any conductive material must have a minimum distance of 4 mm to the front of the terminal block.
Installation by qualified electrician only.
Terminals for protective earth not suitable for any through connection.
Nici o postare găsită